The BACnet.OPC Client can operate as an NT Service by selecting Tools - Options from the menu. This will bring up a dialog box which has a checkbox for selecting NT Service operation. After this option has been selected, then application must be closed, and can only be restarted from the Control Panel - Services Applet. By default, the application will be set to "Interact With Desktop" and will be visible in the taskbar. To make the Service run in the background, uncheck this option from the control panel.
BACnet OPC Client:
OPC Data Access Servers into BACnet. Explorer-style interface. BACnet auto discovery of OPC Tags. Acts as a BACnet Server. OPC datapoints mapped to local BACnet Objects within the BACnet Server. Savable CSV configuration files compatible with Microsoft Excel.
This software will read from an OPC compliant Server and store the information into BACnet Objects stored locally inside the BACnet Server. The BACnet Objects can be read from any BACnet complient device on the network.
An Explorer style interface allows BACnet properties to be easily configured as OPC tags.
BACnet local objects can be configured, modified, and saved online or offline from the OPC application.
Configuration files can be modified in Microsoft Excel.
There are many OPC Servers available, including.
Modbus Lon Any type of PLC.
BACnet BIBBs Supported
DS-RP-A, DS-RPM-A, DS-WP-A, DS-WPM-A, DS-COV-A, DS-COVU-A, AE-N-A, AE-ACK-A, AE-ASUM-A, AE-ESUM-A, DM-DDB-A, SCHED-A
OPC Support Data Access Specification 1.0 and 2.0 and Event/Alarm Specification 1.0
Windows NT 4.0, Windows 2000, Windows XP
This product includes software developed by the Copyright (c) 1999 - 2004 NetGroup, Politecnico di Torino (Italy).
SCADA Engine BACnet OPC Client - Tutorial